Vanesa Morales Posted April 21 Share Posted April 21 Good afternoon forum, I am developing a 60MWdc project, which is planned to evacuate the energy in Medium Tension (34.5kV) through a 5km double circuit line. My problem/question is: I have my 7 BT/AT transformers (6 with 9MVAS and 1 with 3MVA) and with my distances to the MV SE, and, from where a 34.5kV line will come out for 5 km, however, I cannot put that aside, since it only allows me to insert the High Tension evacuation. As you can see, until the Medium Tension Transformers im Ok, but for the 5km, i want to put 34.5kV, not 115kV. How can I enter or consider it? We are thinking of making an "equivalent" of losses of that line within the internal transformers, but I would like to know if there is another methodology to consider it and that not only PVSyst considers that all projects in High voltages be evacuated. Link to comment Share on other sites More sharing options...
Create an account or sign in to comment
You need to be a member in order to leave a comment
Create an account
Sign up for a new account in our community. It's easy!Register a new account
Already have an account? Sign in here.Sign In Now