FOFONE Posted April 18 Share Posted April 18 Hello to all, I am sizing a 10MWp solar plant with PVsyst. At the level of the detailed loss parameters, more precisely the thermal losses, the software proposes me sections of cable going up to 2000m² between the connection box and the inverter. what I find too big. Can you explain me that, why such a section? Link to comment Share on other sites More sharing options...
Create an account or sign in to comment
You need to be a member in order to leave a comment
Create an account
Sign up for a new account in our community. It's easy!Register a new account
Already have an account? Sign in here.Sign In Now