# PVsyst's forum

Welcome on PVsyst's forum.
 It is currently Sat Aug 08, 2020 7:08 pm

 All times are UTC+02:00

 Post new topic  Reply to topic Page 1 of 1 [ 1 post ]
 Print view Previous topic | Next topic
Author Message
 Post subject: How to determine the Wiring loss parameter ?PostPosted: Tue Nov 06, 2012 10:57 am

Joined: Mon Apr 16, 2012 7:29 pm
Posts: 1665
The wiring loss is computed using the equivalent Wiring Resistance Rw of the whole array as basic parameter (calculation R * I² at each hour).
This resistance is calculated "as seen" from the inverter input, i.e.putting all strings, connected to all MPPT inputs of a sub-array, in parallel.

This parameter may be determined in 3 different ways:
- At an early stage, you can specify a generic loss as a percentage at STC conditions (default value 1.5%).
- Then you can calculate this resistance of the array's wiring by yourself according to the effectve wiring properties of your system.
- You have a tool for the evaluation of this resistivity (button "Detailed losses"). This tool asks for the average wire lenghts, allows to determine the wire sections at each stage, for a given loss target at STC. It also evaluates the copper mass, and eventually the wiring cost of your plant. You can define here intermediate junction boxes between strings and inverter inputs.

NB: Wiring losses behave quadratically with the current (R·I²). The loss at 500 W/m² will be half the loss at 1000 W/m² (in %) or a quarter (in [W]). Therefore the yearly energetic losses may only be evaluated on an hourly basis during the simulation, and is depending on the power distribution. The energetic loss appearing in the arrow loss diagram is usually far below your STC definition (in %). The Yearly/STC loss ratio is usually around 60% for the middle-Europe systems.

Top
 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Post new topic  Reply to topic Page 1 of 1 [ 1 post ]

 All times are UTC+02:00

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

Search for:
 Jump to:  Select a forum ------------------ PVsyst SA Announcements (read only)    Latest news - Bifacial Modelling and 3D Drawing    PVsyst's forum rules FAQ (read only)    Installation and use of PVsyst    Meteo data    PV Components    Shadings and tracking    Simulations : parameters    Simulations : results    Standalone and pumping systems Your questions about PVsyst    Howto    Problems / Bugs    Meteo data    PV Components    Shadings and tracking    Simulations    Suggestions    Tutorials : Feedback and requests Links    PVsyst website    YouTube Channel