# PVsyst's forum

Welcome on PVsyst's forum.
 It is currently Sat Aug 08, 2020 8:27 pm

 All times are UTC+02:00

 Post new topic  Reply to topic Page 1 of 1 [ 1 post ]
 Print view Previous topic | Next topic
Author Message
 Post subject: What is the basic concept of inverter sizing ?PostPosted: Tue Nov 06, 2012 10:57 am

Joined: Mon Apr 16, 2012 7:29 pm
Posts: 1673
The inverter power sizing is not a trivial task.
In the system definition dialog, the button "Show Sizing" opens a summary of all sizing conditions, dynamically bound to your definitions.

The upper diagram shows the voltage limits for the number of modules in series: They also show in violet eventual current/power limitations of the inverter specifications, which are not mandatory, except if they are contractual (i.e. if they act on the warranty).

The lower histogram shows an estimate of the power distribution available at the output of the array in your meteo and orientation conditions.
If the inverter is of good quality, it will limit its power simply by displacing its operating point on the I/V curve of the array. In this way, the over-power has not to be dissipated: it is simply not produced. Therefore there is no technical danger to apply an oversized PV array to an inverter, this may operate at some occasions over its nominal power without problems.

The diagram shows that even for undersized inverters by respect to the high-power edge of the distribution, the annual loss may stay very low. The optimal inverter sizing will correspond to a yearly loss between 0.2 and 3%. Above this limit the normal process considers it as unacceptable, but you can change this limit.
The usual values of the PnomArray(DC)/PNomInv(AC) ratio are of the order of 1.25 to 1.30.

This ratio is depending namely on the plane orientation: with a façade system, the maximum power is 2/3 of the maximum at 30° south.

NB1: The nominal power at the DC input of the inverter is higher than the Pnom(AC), by a factor of (1/Efficiency).
NB2: In this tool, the overload loss is only a quick estimation according to this histogram.
The loss calculated by the detailed simulation will usually be lower, as the simulation takes other losses into account in the array behaviour.

Top
 Display posts from previous: All posts1 day7 days2 weeks1 month3 months6 months1 year Sort by AuthorPost timeSubject AscendingDescending
 Post new topic  Reply to topic Page 1 of 1 [ 1 post ]

 All times are UTC+02:00

 You cannot post new topics in this forumYou cannot reply to topics in this forumYou cannot edit your posts in this forumYou cannot delete your posts in this forumYou cannot post attachments in this forum

Search for:
 Jump to:  Select a forum ------------------ PVsyst SA Announcements (read only)    Latest news - Bifacial Modelling and 3D Drawing    PVsyst's forum rules FAQ (read only)    Installation and use of PVsyst    Meteo data    PV Components    Shadings and tracking    Simulations : parameters    Simulations : results    Standalone and pumping systems Your questions about PVsyst    Howto    Problems / Bugs    Meteo data    PV Components    Shadings and tracking    Simulations    Suggestions    Tutorials : Feedback and requests Links    PVsyst website    YouTube Channel