|No. of modules in series
|Page 1 of 1|
|Author:||rraja [ Tue Aug 22, 2017 10:03 am ]|
|Post subject:||No. of modules in series|
Can't able to keep 20 and above Modules in series in PVsyst 6.6.3.
But it was supported in the older versions.
Suggest to solve this.
|Author:||praveenksadh [ Tue Aug 22, 2017 1:27 pm ]|
|Post subject:||Re: No. of modules in series|
There may be possibility that in older version "Lower temperature for Absolute Voltage Limit" set @ 0°C however as per attachment "PV Syst" Set temp. is -10°C resulting 1020V which is exceeding inverter maximum input voltage and not allow to take 20modules in series due to same.
Hence go to Project → Project Setting → Design Conditions and set the "Lower temperature for Absolute Voltage Limit" value as weather file.
Also find below details.
PV Syst Design Temperature.jpg [ 88.04 KiB | Viewed 2410 times ]
|Page 1 of 1||All times are UTC+02:00|
|Powered by phpBB® Forum Software © phpBB Limited