|In sheds arrangement, which power can I install on a given area ?
|Page 1 of 1|
|Author:||André Mermoud [ Mon Mar 30, 2015 4:44 pm ]|
|Post subject:||In sheds arrangement, which power can I install on a given area ?|
The installed nominal power (STC) is directly proportionnal to the collector area:
Pnom [kWp] = Coll. Area [m2] * Effic at STC [%] / 100
Now the Utilization Factor UF (= Acoll / Aground), which is the inverse of the Ground Coverage Ratio (GCR), is calculated according to:
File comment: Utilization FactorWe can notice that the more relevant parameter is the collector tilt: with 30° tilt you can install only 40-50% of the available ground area, when with 4° or less you can install more than 80% of your ground area.
Sheds_Definition_Calcul.png [ 9.24 KiB | Viewed 7628 times ]
This is very weakly dependent on your limit angle.
File comment: UF as function of collector tiltTherefore when the area is limited, you are always advised to put your collectors as horizontal as possible (with the only limit of the soiling problems).
Sheds_Utilization_Ratio.png [ 7.52 KiB | Viewed 7628 times ]
Moreover, this results in much simpler support's mechanics, less wind sensitivity, lower weight, etc.
This allows also to define higher shed's width, i.e. more strings in the width of the shed. This drastically limits the electrical shadings losses.
In most cases, taking the shading effects into account, the overall energy loss will be less than 2-3% with respect to 20-30° sheds.
|Page 1 of 1||All times are UTC+02:00|
|Powered by phpBB® Forum Software © phpBB Limited